If you are planning to **power your house by solar** then you must be wondering about **number of solar panels, battery bank & inverter load you need for your home**. Don’t worry! it’s not just you. These are few common questions that everyone asks if they are planning to **install solar at home**. Today, **SolarClap will address all these question one by one** and also help you out to **calculate solar requirement for your home**.

Before we start teaching the simplest way of calculating the size of solar installation in India, we would like you to remember this fundamental formula:

**Power (in watts) = Voltage x Current**

*Don’t forget this formula as we are going to use it a lot!*

Page Contents

**How to calculate size of solar system in India?**

Most of the solar installations in India are off-grid because our country faces frequent power cuts. Off grid solar installation has 3 key components: **solar panels, battery and solar PCU (solar PCU is a solar inverter with built-in solar charge controller).** To calculate size of solar system, just follow these 5 simple steps:

**Step 1: Calculate your total load that you want to run****Step 2: Size your solar inverter based on electrical load****Step 3: Calculate the total current of your load****Step 4: Decide how many hours of battery backup you need****Step 5: Calculate size of solar panels based on battery size and current of electrical load**

**Calculate your total load that you want to run**

You should know **how much power (in watts) your electrical appliances consume**. For example, a tube light consumes 40watts, fan consumes 80 watts etc. Add the electrical load (in watts) that you wish to use.

Let’s assume that you added everything and the figure that you get is **1000 watts**.

**Size your solar inverter based on electrical load**

Once you know the total electrical load, the next thing that you have to do is find a solar inverter that can power the load. **If your total electrical load is 1000 watts then you should choose an inverter of 1600 watts**. It is advisable to oversize the inverter because unfortunately DC to AC conversion that solar inverters do causes loss of energy. It is also good to know that a **1600 watts inverter comes in 24 volts**. Remember this because we are going to use this fact ahead in our calculations.

**Calculate the total current of your load**

This step is easy! Go back to the formula we taught you in the beginning.

**Power (in watts) = Voltage x Current**

In our example, the **power is 1000** and we already know the **voltage to be 24v**. Let’s insert these figures into our formula.

1000 = 24V x current

current = 1000/24

current = **41.66 amps**

Let’s round it off to 41 amps. Now our solar system needs to generate at least 41 amps of current to power the connected electrical load. Keeping this figure in mind let’s go to our next step.

**Decide how many hours of battery backup you need**

The next step in calculating size of solar system in India is to think **how many hours of backup** you need. Remember, solar PCU/inverter will directly power your electrical load through solar. However, when solar is not available, the solar energy stored in batteries can be used to power load. Let’s say you need backup of 5 hours. Now there is a very simple formula to calculate size of battery based on your total load and backup time required.

**Total load (in watts) x hours of backup needed / 24**

Why should we divide by 24? Because our inverter is 24v.

Let’s put the figures from our example in this formula:

1000 x 5 hours / 24 = **208**

Let’s round it off to **300Ah** because it is OK to have **extra backup**!

You can install 2 batteries of 150Ah.

**Calculate size of ****solar panels based on battery size and current of electrical load**

Yes, sizing of solar panels comes at the last because **solar panels are either going to feed the battery or run electrical load**. They need to **produce enough voltage and current** to charge the battery properly and to run electrical load. So how do we decide the **size of solar panels**?

Time to remember our fundamental formula again:

**Power = voltage x current**

And let’s give you another golden formula which will help us here:

**Charging Current of Battery = 1/10th of its Total Ah.**

This means if we have **300Ah battery** then **charging current of battery is 30 amps (1/10th of its total)**. Our solar panels need to make 30 amps of current to feed our battery bank.

But what about the electrical load? Let’s not forget about that. We already calculated that our electrical load will need 41 amps to run. We need to add this to the amps that our battery bank is going to take.

Hence, **30+41 = 71 amps**.

Our solar panels should make **71 amps**.

**#Fact: On an average, 250 watts solar panels have a voltage of 30v.**

Now, let’s put everything together in our fundamental formula:

**Power = Voltage x Current**

**Voltage:** 30 V

**Current:** We calculated in the last step that we need **71 amps** (30 amps to feed the battery bank and 41 amps to run the electrical load directly through solar).

Power = 30 x 71

Power = **2130 watts**

Let’s round it off to **2500 watts** because you can’t have 2130 watts panels.

**This is our answer: **We need to install panels of 2500 watts to feed our battery bank and run electrical load.

You can go for 10 panels of 250 watts each.

Simple! Wasn’t it?

We hope that **SolarClap** helped you understand **number of solar panels, battery bank & inverter load you need for your home**. If you are looking forward to purchase solar products for your home then do check out this **list of top 10 best solar panels in India**.

**Note:*** Please consider this as an honest attempt from SolarClap to simplify complex ideas and calculations. We do not claim that this is 100% accurate. There are other things to consider such as power factor of inverter and other technical things. Always ask an expert to size the solar system based on unique needs for your home.*

Got Queries? Ask with **#SolarClap**

Simple yet need to be rectified dear, Considering AC loan and calculation with DC 24V doesn’t make sense.

Way cool! Some very valid points! I appreciate you writing this write-up and also the rest of the website is extremely good.

Thanks for your kind words.

My brother recommended I might like this web site. He was totally right. This post truly made my day. You cann’t imagine just how much time I had spent for this information! Thanks!

Thanks for commenting.

good thanks sir for inform us thanks again

Glad you liked it.

if we install 2500 watts solar power with 1600 watt inverter it will be damage inverter because u cannot give extra watt to inverter to its range.

Thanks again for the blog post.Much thanks again. Fantastic.

helped me a lot for calculating the number of inverter requirements

Fantastic goods from you, man. I’ve understand

your stuff previous to and you are just extremely magnificent.

I actually like what you’ve acquired here, certainly like what you are

saying and the way in which you say it. You make it entertaining and you still care for to keep it wise.

I can not wait to read much more from you. This is actually a terrific

site.

Nicely explained but you perhaps forgotten to divide the load by daily available sunlight time. Hope you will rectify.

Hi there! I simply would like to give you a big thumbs up for the great info you have got here on this post.

I am returning to your web site for more soon.

It is appropriate time to make some plans for the long run and it is time

to be happy. I have read this publish and if I may I wish to suggest you some interesting issues or

advice. Maybe you can write subsequent articles relating

to this article. I want to learn more issues approximately

it!

Hello there, I found your site by means of Google even as searching for a

similar topic, your web site came up, it looks great.

I have bookmarked it in my google bookmarks.

I was just seeking this info for some time. After six hours of continuous Googleing, finally I got it in your web site. I wonder what is the Google’s problem that doesn’t rank this type of informative websites closer to the top. Usually the top sites are full of garbage.

Thank you ever so for you post. Really Great.

Thank you ever so for you blog post.Really thank you! Fantastic.

Major thankies for the blog.Much thanks again. Really Great.

I think this is among the most vital info for me.

And i am glad reading your article. But want to remark on some general things, The website style is great, the articles is really great :

D. Good job, cheers

Truly appreciate the information you illustrated

How can I get in touch with you to discuss possible cooperation

Regards

Simple and easily understandable

One 250 volt solar panel generates how many units of current from morning to evening, during summer & how many units in cloudy /winter.

Very educative and has answered some intending questions.